1. Connect your smartphone to the pump via Bluetooth
After start-up the ProMinent App searches for available Bluetooth devices and displays a list of the pumps it has found. A connection is possible with pumps marked as "reachable". The selected gamma/ X pump is indicated by flashing of the blue LED.
2. Enter the security code
When the Bluetooth connection has been established, the four-digit security code is requested. The entered code is sent to the pump for verification with "OK". (Note: After three incorrect attempts, access to the gamma/ X pump is blocked for safety reasons.)
3. Control functions with the context menu
When the correct PIN has been entered, the context menu of the gamma/ X pump is opened. This menu is used to access all important functions:
> The switch next to the pump image starts and stops the pump function.
> The pump can be renamed by touching the pump name.
> The left arrow next to the pump image terminates the Bluetooth connection to the pump.
> The symbols on the right-hand side show the functions of the list entries:
• An arrow opens an additional menu.
• A check mark results in an immediate change.
• The information symbol is provided purely for display purposes and cannot be used to change values.
4. Enter numeric values
Values can be entered either with the number indicator or roughly with the scroll bar. Select "Apply" to enter the new number or the back button to cancel the change.
5. View device information
This provides view-only information on the options and settings of the currently controlled ProMinent gamma/ X pump. It is not possible to enter values.
6. Expert settings
Here it is possible to enter settings for the suction and pressure stroke, pressure limits etc. of the ProMinent gamma/ X pump.
7. Non-numeric values
Non-numeric values such as the required reaction to air intake are programmed by tapping the desired option. The change is cancelled by pressing the back button.
8. Dynamic menu adaptation
The menus adapt dynamically to the selected settings. If, for example, the analogue mode is changed from "0..20 mA" to "linear", additional setting options for this pre-setting are displayed.